90° Tee and Cap MF x 150mm VIT Smooth Pipe.
Perfect Welding and Finish. VIT-Smooth is the new industry standard when it comes to welding and finishing of vitreous enamel. The welds are almost invisible. All the welds on bends are ground down so they are totally smooth. The texture and colour of the enamel is very matt black so matches most stoves much closer than competitors.
VIT-Smooth uses 1.2mm thick zero carbon steel, then coats of powdered enamel are added giving a total thickness of 1.4mm to 1.5mm. Compare this to most competitors 1.0mm steel or thinner!
Suitable for gas, oil and solid fuel appliances with temperatures up to 750 degrees C.
Stove pipe should only be used as a connecting pipe between your appliance and Flue Liner / Chimney Stack / Twin Wall Flue System.Black stove pipe should NOT be used to pass through ceilings or walls. CONSTRUCTION
Black stove pipe is a single skin flue system manufactured in zero carbon steel with vitreous enamel coating in a matt black finish.
Suitable for gas, oil and solid fuel appliances with temperatures up to 750 degrees C INSTALLATION
You should not install a piece of Black Stove Pipe within 3 times the diameter of the flue from combustible material, e.g. wood, plaster boards, etc.
A 4 inch (100mm) diameter piece of Black Stove Pipe should be 12 inches (300mm) away from combustible materials.
When installing make sure Black Stove Pipe is installed the correct way up - the smaller diameter should always be pointing downward.
This is because all the condensates will stay within the flue system and not pass to the outside of Black Stove Pipe.
Each joint should be coated with a jointing compound (fire cement or high temperature silicone sealant).This makes sure that no condensate can escape and spoil the appearance of the pipe. MAINTENANCE
You should make provision for inspecting and cleaning the chimney. This is particularly important on solid fuel applications.
You can acheive this by installing a black pipe with an access door.
It is recommended that chimneys serving solid fuel appliances be swept and maintained as frequently as necessary but at least once a year.
||90° Tee and Cap MF 150mm
||Zero Carbon Steel